• This construction will be used for fans with rotor diameter greater than 1,600 mm in double suction.
• The rotor is supported on two bearings, whereas these bearings are on opposite sides in relation to the rotor (double-supported).
• The concrete base will feature cut-outs and/or overhangs for an improved fit of the machine and a reduction in the amount of concrete needed to build it. It will be up to the supplier to manufacture and supply a metal base destined to secure the bearing as well as to be used as the motor rail.
• The supplier will carry out the pre-assembly in its factory, correcting any possible manufacturing faults as required, in such a way to avoid delays during final assembly
|Model No.||Special design||Foundation arrangement||Steel structure|
|Motor Power||110KW~ 8000KW or larger||Concrete foundation with anchoring bolts|
|Driven type||Direct by coupling||Option accessories||Filter , silencer, expansion joints,|
|Impeller size||Up to 4000mm||inlet/outlet damper,|
|Dimension||Special design||Pneumatic /electric actuator,|
|Flow||Up to 1500,000 m3/h||Monitoring instruments for the Bearings|
|Pressure||Up to 30,000Pa||Material||Carbon steel / Stainless steel|
|Gas Temp.||-20~500℃||Cooling type||Air/water|
|Speed||Up to 3600RPM||Seals type||Labyrinth / Carbon ring/ N2 sealing|